McCormick has been the company to turn to for flavour expertise since 1889. In the Foodservice division of McCormick (UK) Ltd, they provide a range of herbs and spices for restaurants, chefs and catering establishments. Schwartz is the forerunner brand in their portfolio.
Mitie Technical Facilities Management has called to assist with issues to the Climaventa water chiller serving Air Handling Units within the McCormick factory. The chiller had not functioned correctly for some time, but with hot weather over summer months it made the working conditions rather uncomfortable for factory staff.
Following a survey Adcock engineers quickly identified the faults and carried out the replacement of a large 7kw water circulation pump and pipework manifold, along with pump relays and contactor.
They also changed the pressurisation unit and strainer. Finally the refrigeration circuits were both pressure tested, leaks repaired, PRVs replaced and the system re-commissioned.
Our fast approach and vast knowledge and experience of working with water chillers led to the system operating efficiently again and able to maintain the correct temperature within the factory
Get monthly “Airmail” straight to your inbox. Sign up today to receive your first issue.
You can opt out at any time.